Our Kambic material hatches can be individually customized to your requirements. You determine dimensions and accessories, we manufacture and assemble according to your wishes.
Following order number defines the make-up of your equipment; we are more than happy to assist or send you a tailored quotation. Frequently ordered product variants can be found in the examples below.
|Interior [mm]||Exterior [mm]||Options|
|PB 6/6/6 UV||600||600||600||700||850||750||UV-C surface sterilization|
|PB 6/6/6 HUV||600||600||600||750||970||750||Internal air circulated and cleaned via HEPA filter
UV-C surface sterilization
|PB 6/6/6 AIR||600||600||600||700||700||750||Air shower with supply from HVAC system|
|PB 6/6/6 EL||600||600||600||700||750||750||Electrical interlock|
|PB 8/10/8 LUX||800||1000||800||1000||1150||950||Floor installation|
|PB 6/6/6 90°||600||600||600||*||*||*||Corner installation|
Option for surface sterilization. Utilizing the mirror-polished surface, even complex shaped loads can be illuminated from all sides through reflection. A customer adjustable timer can initiate a program sequence to be started, where a a red/green indicator signals both sides that a sterilization is in progress. 99% of harmful UV-C radiation is already filtered by the 12mm tempered safety glass, and thus does not penetrate to the outside. The residual radiation is absorbed by an additionally applied film. The UV-C light is automatically switched off if either of the two doors is opened. An hour counter (individually adjustable) records the operating hours of the UV-C tubes and warns when they need replacing. This option can be turned off, if the effectiveness of the UV-C light is validated otherwise.
Option for cleaning the load by means of air. A laminar air flow is generated inside the hatch, which is purified through a HEPA filter. A differential pressure indicator shows the degree of contamination of the filter. An option to connect to the internal HVAC system is also provided.
The doors contain access openings which can be used to flood the chamber with H2O2 for disinfection.
Required if two rooms require connecting past a third.
Other topics that may interest you: